The typical life of a furnace filter is 3 months. This can vary based on how much the fan is running, how dirty the ducts are, and the lifestyle of the tenant/homeowners. Pet hair and dander can be a significant factor as well. The best way to gauge how often the furnace filter needs to be changed is to check it often and see how dirty it gets.
You should never let the filter get to the point when you hold it up to the light and only 50% of the light is visible looking through the filter.
A good rule of thumb if you live in Denver, CO is to replace the filter in the fall when the furnace first starts running a fair amount. Replace it again at the end of January and if you forget to check it again at least you are changing it twice a year and this should be good enough to make sure it is pretty clean. If you have a two stage high efficiency furnace the fan will tend to run more often so you may want to change it January first and again in Mid March.
If you have central air conditioning, then it’s a good idea to check the filter monthly in the summer to make sure it is clean. Changing every 2-3 months is usually sufficient.
It is more important to check and replace the filter than to pay extra for an expensive filter you only change once a year. Having a clean filter will extend the life of your furnace and can save you a significant amount of money by following a maintenance schedule.
Is your furnace not starting up and maybe making a funny sound like it is trying to start up? Perhaps you have shut it off and then turned back on. Maybe you just turned the fan on and it works. You may be in need of a new induced draft motor or draft inducer motor. This motor is what creates a draft through the heat exchanger. Air and gas are drawn through the front of the furnace and conveyed to the flue connector. What you have is a whole assembly. In most cases the entire assembly is what gets replaced. In some rare cases you can replace just the motor which is cheaper but takes longer to do. When replacing the assembly it is important to replace the gasket that goes between the assembly and the heat exchanger manifold. The gasket is usually fiberglass or fire rated foam. Modern furnaces have this motor as well the circulating or blower motor. Out of the 2 motors, the inducer motor typically is the one that fails first. The bearings start to wear out making the operation noisier and eventually they fail and the motor stops turning. I have seen motors with noisy bearings run for a long time (years) and in other cases no increased noise is noticed before the motor fails.
The induced draft assembly is typically made of steel or metals such as the one in the picture.
They often develop rust and wear out. Replacing the draft inducer motor assembly is the only way your furnace will operate.
How much should I expect to pay to replace my draft inducer motor assembly?
Depending on the make and model expect to pay between $500 and $800 for residential gas furnaces. At Tobin you can count on us to tell you what the problem is and give you a fair reasonable price ti install a new draft induced motor.
Give us a call for a quote if you are in the Denver Metro area 303.893.5675
"TOBIN recently replaced two 27 year old furnaces in my house. They did a fantastic job in both planning the job and installing the furnaces. They were very professional, worked very cleanly and cared about getting the installation perfect. When they answered my numerous questions, you could tell they answered with a wealth of experience and knowledge. This is a great company you can trust."
- Brian Thomas
"Great Service. My furnace was short-cycleing and would shut off right after it turned on. They came really quickly, cleaned the parts and didn't charge me more then the service fee. They were very professional and nice. A really good family owned company. I would highly recommend."
- Brie Cook
"My furnace went out and I called up TOBIN to get an estimate. I had three other estimates for similar furnaces and the other companies wanted $1000 more. I hired TOBIN and had a high efficiency Amana furnace installed for much less than the other companies. I was very happy with the two service technicians who came out. They had to do some additional piping to vent the furnace and everything looked neat and clean when they were finished. I highly recommend the professionals at TOBIN."
- Bryan Murphy
TOBIN Heating & Airconditioning is the Denver's Most Trusted & Affordable Heating & Air Conditioning Service Since 1954 – Family Owned And Operated.